Circular bare copper-conductor of stranded wires to HD 383
Inner semi-conducting coating
Conductor insulation of cross-linked Polyethylene (XLPE), PE-compound DIX8 to HD 620.1
Outer extrusion of semi-conducting coating spliced with the insulation
Wrapping of conductive material
Shield: Braiding of copper wires with one or two tape(s) applied helically
PVC outer jacket, compound DMV6 to HD 620.1
Jacket color: Red
Suitable for installation mostly in power supply stations, indoors and in cable ducts, outdoors, underground and in water as well as for installation on cable trays for industries, switch boards and power stations. Due to the good laying characteristic, this cable can also be installed in difficult in difficult line guide ways.
The inner conducting layer between the conductor and the XLPE insulation and the firmly bonded outer conducting layer on the XLPE insulation assures a construction free of partial discharges with high operational reliabilities.
During installation up to -5°C/+23°F
Short Circuit Temperature
+250°C/+482°F (short circuit duration up to 5 sec.)
U0/U 6/10 kV, 12/20 kV, 18/30 kV
Operating Voltages for
6/10 kV = max. 12 kV
12/20 kV = max. 24 kV
18/30 kV = max. 36 kV
Test Voltages for
6/10 kV = 15 kV
12/20 kV = 30 kV
18/30 kV = 45 kV
Minimum Bending Radius
During Installation Max. 15x Cable Ø
Power Ratings Table
See Technical Information
|NO. Cross- Section Area||Copper Wire Screen Area*||NO. Sheath Thickness||NO. Overall Diameter||Approx. Weight|
|N2XSY/ N2XSH CU||N2XS2Y CU||N2XS (F) 2Y CU|
|mm2||mm||mm||mm||kg / km||kg / km||kg / km|
There is no news related to this product.
ZMS Cable have a wide product scope, includes: Power cables up to 500kV, AAC, AAAC, ACSR conductors, ABC Cable,electric wires, instrument cable, telecommunications cable, Stay wires. With advanced manufacture technology, rich human resource and effective management system, we guarantee all products are manufactured strictly in accordance with GB, IEC, BS, NFC, ASTM, DIN standards,etc. Beyond quality control, ZMS have been trying its best to offer much higher standard of services rather than expected.