Cu (AL) /XLPE / Copper Tape Screen / SWA (STA) / PVC Power Cable (3 CORE) | Cu (AL) / XLPE / Copper Wire+Copper Tape Screen / AWA (ATA) (1 CORE) / PVC Power Cable
Single Core / Three-Cores XLPE PVE insulation power cable can be arrranged according to GB standard, Internation IEC standard, Ameica ASTM standard, British BS standard, etc.
XLPE Cable With Copper Wire Screen
Integrated intelligent high voltage XLPE cable can online monitor the operation parameters during the operation of high voltage cable.
It can online real-time monitor cable actual operation temperature and then realize online temperature measurement and control, online fault location and improve the operation load of cable system.
Besides, it also can accomplish online monitoring of partial discharge, current carrying capacity and outer sheath condition.
It can provide important specification judging evidence for cable safety operation and more load operation, ensure the cable safety operation, extend cable service life, develop the cable transmission capability to the deepest extent, reduce the operation cost, meet the requirement of customers, safety and economy.
It decrease the replace frequency, reach energy saving and consumption reducing, increase utilization of transmission energy, achieve the best effect of transmission performance of XLPE cable.
XLPE PVC Insulated Power Cable of ZMS have great economic benefit and social benefit.
Medium voltage cables for distribution networks; also for connection to generation units and plant and process connection.
To be laid directly in ground, outdoors, indoors and in cable ducts.
DIN VDE 0276-620, HD 620 S1, DIN/BS EN 60228,BS EN / IEC 60332-1-2
Rated voltage: Uo/U:3.6/6kV, 6/10kV (11kV), 12/20kV (24kV), 19/33kV, 26/35kV (35kV).
No. of core: Single core or three cores.
The highest allowed operating temperature of conductor for long-term working is 90oC. In short-circuit (Max. long-term is no more than 5 seconds). The highest temperature for conductor is no more than 250ºC.
D.C. resistance of the conductor complies with the stipulations of 12/20kV (24kV).
The environment temperature should be no lower than 0`c when lay. Otherwise it should be preheated.
The PVC insulated power cable is laid without horizontal drop limit.
Working Frequency Voltage Test: 3.5Uo/5min without puncture.
Partial Discharge Test: The discharge volume should be no more than 10pC under 1.73Uo for the cable.
Minimum Bending Radius
Single core - Fixed: 15x overall diameter
3 core - Fixed: 12x overall diameter
(Single core 12x overall diameter and 3 core 10x overall diameter where bands are positioned adjacent to joint or terminations provided that the bending is carefully controlled by the use of a former)
|Conductor||Class 2 Stranded Copper or Aluminum Conductors for Single Core and three-Core Cables|
|Inner Semi-Conductive Layer||Semi-conductive material|
|Insulation Halogen Free||XLPE (Cross-Linked Polyethylene)|
|Outer Semi-Conductive Layer||Semi-conductive material|
|Insulation Screen||Semi-conductive XLPE (Cross-Linked Polyethylene)|
|Screen||Copper wires or Copper tape|
|Armour||Single core: AWA (Aluminium Wire Armoured)|
Multi-core: SWA (Steel Wire Armoured)
|Sheath||PVC (Polyvinyl Chloride)|
|Temperature Rating||Fixed: -20°C to +70°C|
Flexed: -5°C to +70°C
|Short Circuit Temperature||+250°C|
|Minimum Bending Radius||15x overall diameter|
There is no news related to this product.
ZMS Cable have a wide product scope, includes: Power cables up to 500kV, AAC, AAAC, ACSR conductors, ABC Cable,electric wires, instrument cable, telecommunications cable, Stay wires. With advanced manufacture technology, rich human resource and effective management system, we guarantee all products are manufactured strictly in accordance with GB, IEC, BS, NFC, ASTM, DIN standards,etc. Beyond quality control, ZMS have been trying its best to offer much higher standard of services rather than expected.