H05V-K / H07V-K Conductor
Class 5 flexible copper conductor according
BS EN 60228 (previously BS 6360)
PVC (Polyvinyl Chloride) Type TI1 according to BS EN 50363
Fixed: -30°C to +70°C
Flexed: -5°C to +70°C
12: 5 x overall diameter
12: 6 x overall diameter
Red Black Blue Orange Yellow White
Green Grey Brown Violet Pink
Single croe and Multi Core Ruber Flexible Cable. Soild or Stranded Plain copper, PVC insulated and PVC sheathed.
Single Core: Brown or Blue
Two Core: Brown and Blue
Three Core: Brown, Blue and Green / Yellow
Four Core: Green / Yellow, Black, Brown and Blue
Five Core: Green / Yellow, Black, Brown, Blue and Black
Sheath Colour: Grey
Other colours Available to order.
Minimum Bending Radius: 10 times
Maximum Conductor Temperature: 70°C
Maximum Conductor Temperature During Short Circuit: 160°c
BS EN 50525-2-31 (previously BS 6004, Cenelec HD21.3) BS EN / IEC 60332-1-2
PVC panel wiring for use in the switch control, relay and instrumentation panels of power switchgear and for purposes such as internal connectors in rectifier equipment, motor starters and controllers.
We are PVC Insulated and PVC sheathed Single Core and Multi Core Cables Manufacturers and Suppliers, provide PVC Insulated and PVC sheathed Single Core and Multi Core Cables wholesales and PVC Insulated and PVC sheathed Single Core and Multi Core Cables price.
|Nominal voltage Uo/U||[V]||300 / 500 volt 450 / 750 volt|
|Temperature range||in motion||+5°C till +90°C|
|Operating temperature||short circuit||°C||250|
|Short circuit time||max.||[sec]||5|
|Bending radius||one time / fixed||x diameter||6|
|H05V-K H07V-K||IEC 60332-1|
There is no news related to this product.
ZMS Cable have a wide product scope, includes: Power cables up to 500kV, AAC, AAAC, ACSR conductors, ABC Cable,electric wires, instrument cable, telecommunications cable, Stay wires. With advanced manufacture technology, rich human resource and effective management system, we guarantee all products are manufactured strictly in accordance with GB, IEC, BS, NFC, ASTM, DIN standards,etc. Beyond quality control, ZMS have been trying its best to offer much higher standard of services rather than expected.